I will try not to bug you fellas too much, but you never know...haha
To address the knob and tube in the attic, I ran all new branch circuits from the subpanel in the closet. Once the main is hooked up, I will tie the subpanel in and be good to go.
This thread is awesome!!!!
JB Sparks wrote:Right on Yanche, The new code requires that a bonding means located at and outside the metersocket be provided for grounding of the cable tv and tel interfaces. the cheapest way I found was to use a short grounding bar that comes with it's own mounting angle bracket and mounted it right beside the socket.
sorry Hunlock, I forgot to mention that, us old timers kid each other everytime we forget something by saying " You can't think of everything"!! That and we would say if I carried everything on the truck that I needed I would be driving a tractor-trailer.
BTW haven't mentioned it on this site yet but, the wife and I have decided that it is time for me to hang it up. I told the contractors I do work for that I will finish up the projects we have going but that will be it, start looking for another electrician. Now maybe I can get our kitchen remodel completed that I started a year ago this month and at best is only half done.
Good luck on the service change Hunlock, while you are doing the work and you get stuck on something just give a shout and we'll be happy to bail you out.