CoalBurner5 wrote: ......
Would it make a big difference to move the stove pipe and if I do decide to move the stovepipe for a more direct route outside the house, where should i locate the barometric damper?
GIve me feedback for which would be the best location.
Already been answered by member Berlin in this thread.
Berlin wrote:no need to be overwhelmed, all you need to do is raise the height of the stack with tile AND brick to be about 1' above the closest peak. Next, run the smoke pipe between the boiler and the stack at around a 45º angle so it takes the shortest route between the boiler and chimney, then move the baro from the bull end of that "T" to a "T" in the middle of the straight run of smoke pipe.