First day of set up and testing complete, passed the low and high voltage test and got preliminary set up completed for high limit test and others tomorrow. Some preliminary numbers to consider:
Flue Temp 275*F
Flow rate 24 gallons in 3.5 minutes (6.85 GPM)
Consider the formula BTUH=GPM X 500 X DeltaT in Degrees F, we are looking at some fantastic numbers! But the flow calculation was taken off a standard water meter and our observation might be off, if it is correct here is a fantastic number, 274,000 BTUH! Based on the flue temp it appears that the boiler is 88% efficient or better, more to follow after tomorrows testing.
Here are some specs on the boiler:
Same feeder as the 220 furnace (dual Pocono 110 burners)
48.5 Square feet heating surface
42 gallon water capacity
320 # hopper with 23X17X11 ash pan
Honeywell 7224C Triple Aquastat
Honeywell 6006 High Limit Aquastat
Same Timer Relay and Rheostat controls for the idle circuit as the WL 110 boiler
5 GPM DHW coil
Approximate package weight is 1,200#, boiler base and Pressure vessel are easily separated for movement of boiler
Stay tuned form ore results tomorrow night, thanks for listening!