Here is the basic: A 120v BRK interconnectable CO detector with a BRK relay (RM4) rated at 15A, 1/3 HP triggering the NC contact to open. You can also use Kiddie brand, but their relay contacts are rated at 10A.
This is an option: You can use both contacts (NO/NC) connected to an outlet, one will open while the other closes. You will have to break the hot side tab on the outlet that connectes them together so they can work independantly. This can deactivate the stove while activating another item (an exhaust fan, garage door, lights).
Last edited by mariohotshot
on Mon Nov 04, 2013 11:55 pm, edited 2 times in total.