I looked at a few of your older posts and ran across this one: questioning BTUH calc
I am heating nearly 5,000 sq ft of home with alot of tall ceilings. My trophy room alone is 1,200 sq ft with 14' tall ceilings. There are other tall ceilings in the house as well. It is a newer home with proper insulation and I live in Winchester, VA, 2 hrs south of Harrisburg, pa.
Considering the "volume" you are keeping at 70 degrees, 1.5 tons per month in the middle of winter seems pretty good! How much LP & electric were you using previously?
As I recall your EFM is in a detached garage...any change the garage is unheated and the boiler is uninsulated?
mooseman100 wrote:I am set at 4 teeth, the lowest it will go, 4 1/2 air.
Do you need the air at 4.5 to get a proper burn? Don't use more air than necessary to get a proper fire & ash ring.
mooseman100 wrote:Since water is circulating nonstop I did not put a loop on my main outside of furnance.
I don't understand that statement.