Hi from RI..I have the same boiler..I have had my WL110 since April, and have been using it ever since..right thru the summer..
I have a couple of opinions to offer about your settings...
LL 130 both w/ 10 diff.
First of all..why do yo have them set so low at this time of the year? For a barn your size, if we get any real Winter weather, I think you may be a bit chilly!
- I believe the spread between your H and low should be between 20-25... I think 32 is too much..
I would suggest 160LL and 180HL
10 min. off 24 sec. on /Rheostats, pusher min. fan about half
-This may work for you now, but pretty sure only because of periodic calls for heat..I think you will find that the 24 sec. on time will cause you to have out fires once the weather moderates even more going forward...you can prolly get away with about 8 off 42, or 7 off 32 on in the months ahead.
Draft .01 WC on the base at smoulder, .025 on fire
-I believe these settings are too low..You should have your over the fire draft between .03-.04.
..In speaking with Matt, I have always heard him say the base reading should be about .02-.025...Actually, he has said that when you see the base reading DROP to about .01, then that's a good indication that you are in need of a cleanning....I think you need more draft
How do u like Kimmel rice? I can only get Blaschak here in Southern NE..where do u get that from? how much?
BTW...Be Glad you have a manual at all!
... Those of us who purchased early on didn't have such a luxury for many months!..right Matt?