My other stove, I didn't run a draft gauge or baro. I know my Stack Temps were 250-300 Normally.
(Temps taken INSIDE the pipe with a probe just before the chimney)
NOW, I have been running the LL Hyfire, baro, Coaltrol, Draft Gauge, etc...for 3-4 weeks now, the draft has been .02-.04 normal, but when the stove gets really cranking, it creeps up to .05-.06 and the baro opens about 1/4 - 1/3 open, the internal pipe/stack temps are around 200-225, if I push the baro open a bit farther, the draft settles back down to .03-.04 (approx.) and the stack temps drop 20-30 degrees.....
I am already at the limit of the Baro Weight (.02), I put an extra screw for adjust of the weight on the flapper to open a bit sooner.
When it starts getting much colder and the chimney starts drawing more and stove runs a bit hotter to keep up, should I adjust anything or does everything seem okay.??