Gentleshepherd wrote:Photo 1 Shows damper closed when furnace is firing
Photo 2 Shows Damper whne furnace is done firing.
Photo 3 SHows damper about 30 seconds after furnace is done firing.
Everything seems to be working properly, no issues. Any comments would be appreciated.
Gentleshepherd wrote:I have a Hot Air Keystoker and I re-routed my furnace pipes today and move my barometric damper from the end of a T to the MIddle of a T and it is now on a Diagonal T. I fired up my furnace today and can't get the damper to close. It stays open all of the time and that's even with the control set to the lowest or highest bracket. My question is this, can I run it with the damper open full bore? I can't get anyone local until Monday to look at it.