hello just helped a neighbor install his ka-6 2 weeks ago and it seems to be running pretty good. I was reading the set up instructions from keystoker about the air shutter on the main stoker blower. we set the draft with a draft meter over a full fire and was able to achieve .02 draft with the barometric damper. after looking at the stoker tonight the air adjustment is in the fully closed position from the factory. should I open it up half way per keystoker instructions and then adjust the barometric damper to .02 or should I leave it alone? the ka6 is using a regular chimney with very good draft. I have a kaa-2 and I only have the one air adjustment on mine so I am curious what to do. my other question is what should the the average pounds per day be to heat a 2800 square foot log cabin with cathedral ceilings be. he been burning about 100 pounds in 24 hours with outside temps in the 0-20 range and indoor temps of 68 degrees.