ShawnTRD wrote:Thanks Rob
Didn't think about the tees. I have to go about four feet to the right from the back of the boiler to the chimney. Should I have the pipe go in angle or an extra elbow and keep everything vertical and horizontal?
Can the tee at the bottom be set at an angle? I think it will be about 60 degree angle. Also I have about 22" from the sheetrock to the body of the boiler. Think that's more then enough? Keystoker says 18" to remove DHW coil if needed.
lzaharis wrote:I would not leave that chimney by itself with no external anchorage Shawn.
ShawnTRD wrote:Also what do I need around that clay flue for a thimble? Example?