Salemcoal wrote:I am installing a vf 3000 in my garage which will run in series with my oil boiler in the cellar. I have already run and burried my feed and return plus lines for DHW. I forgot to run a wire for the thermostat. Any suggestions? Thanks
you don't need tstat wires to the house.
the word tstat is very confusing when installing the vf3000.
the wall tstat that comes with the vf3000 dosen't get used for anything (throw it in the garbage).
when you read about connecting a tstat wire, it means connect a wire from the A350 johnson controller N.O. relay to the tstat terminals on the VF3000 control/timer box.
you don't need any wire running from thr vf3000 to your oil burner.
the Vf3000 will monitor the water temp and keep it at the temp setting of the A350.
when the oil burner starts the circulator the baseboard water will flow into and out of the VF3000... the water temp will drop and the A350 tstat N.O. relay will close and turn on the stoker.
trying to get DHW out of the remote VF3000 might be a problem if there is a long pipe run to the oil burner.