steveyrock wrote:Boiler is coming along very good but I need to know if my room thermostat gets connected to the A350 control anong with the feeder and oil gun thermostat wire? it is a duel boiler, oil and coal. Do I connect it to the same terminals?
hey stevyrock I can see you have been very busy!!!
I don't think you need that thermostat supplied with the VF3000.
I assume you have a wall thermostat up stairs in your house.
is it high voltage or low voltage?
if it is low voltage (24v ac) you will need to buy a switching relay like this:
This link is broken, either the page no longer exists or there is some other issue like a typo.
This you will use to turn on the circulator for heat.
if you have high voltage thermostat up stairs you can wire it directly to the circulator.
The VF3000 dosen't know anything about your wall thermostat.
If you wired the oil gun as shown in the oil burner kit, you should be able to set the A350 to 140 degrees
and supply power to the gun and the a350 will fire the gun until the temp gets to 140* and then it will turn it off.
your set up looks a little to close to the oil tank....but it's hard to judge distance from a picture.
in New york state you need 10ft between a oil tank and a boiler.... it may be different where you are.