We have returns of gauges with false readings. Drain to zero pounds and see if the needle is stuck. If the gauge creeps up, especially if it creeps up as the temperature increases and then blows off, you probably have a pinhole leak in your domestic water coil.
Cut off the water supply to the coil on both ends and see if it stops, after you've drained to zero pressure. If it stops, the coil is bad.